Nibe F205P heat pump produces very low pressure hot water.
Hot water pressure is strong when you first open a tap but then gradually reduces to a trickle.
The fault is a Pressure Reducing Valve (PRV) is faulty.
Replace the PRV. Replacement part is - 520-467-0829 Pre-Set at 3.5 Bar - 330 Series Domestic Pressure Reducing Limiting Valve with Cold Take Off - PRED330006
Isolate water from the mains stop cock before replacing the part.
|< Go Back||2017-07-09|